Mobile submersible sewage pump non-blocking 960~2950 r/min Speed
industrial sewage pumps,
stainless steel sewage pump
Mobile submersible sewage submersible sewage pump non-blocking
QW (WQ) type submersible non-clogging sewage pump repair and maintenance:
QW (WQ) type submersible non-clogging sewage pump with a unique impeller structure and a new mechanical seal, can effectively transport containing solid and long fiber. Impeller Compared to conventional impellers, the pump impeller is in the form of a single or double runner, which is similar to a pipe with the same cross-section size, with a very good overcurrent, with a reasonable spiral chamber, making the pump efficient High, impeller static and dynamic test, so that the pump in the run without vibration.
QW (WQ) type submersible non-clogging sewage pump conditions of use:
- medium temperature does not exceed 60 ℃, medium heavyness of 1 ~ 1.3kg / dm3.
- no internal self-flow circulation cooling system of the pump, the motor part of the liquid surface does not exceed 1/3.
- cast iron material used in the range of PH5 ~ 9.
- 1Cr18Ni9Ti stainless steel material can use the general corrosive media.
- the use of environmental altitude of not more than 1000 meters, more than when the order should be made in order to provide you with more reliable products.
Note: If the user has a special temperature, media and other requirements, please specify when ordering the details of the transmission medium, so that the unit to provide more reliable products.
QW (WQ) type submersible non-clogging sewage pump Features:
- QW (WQ) type submersible non-clogging sewage pump with a unique single leaf or double blade impeller structure, greatly improving the ability of dirt through the submersible sewage pump can effectively pass the sewage pump pump diameter 5 times the fiber material and diameter Sewage pump pump diameter of about 50% of the solid particles.
- QW (WQ) type submersible non-clogging sewage pump mechanical seal using a new type of hard corrosion-resistant tungsten carbide material, while the seal is improved to double-end seal, so that long-term operation in the oil chamber can make the submersible sewage pump safe continuous operation 8000 Hours or more.
- QW (WQ) type sewage pump overall compact structure, small size, low noise, energy saving effect is obvious, easy maintenance, no need to build pump room, dive into the water to work, greatly reduce the project cost.
- QW (WQ) type submersible non-clogging sewage pump seal oil chamber is equipped with high precision anti-jamming leak detection sensor, and stator windings embedded in the thermal element, the WQ submersible sewage pump motor absolute protection.
- According to the needs of users with automatic safety control cabinet, submersible sewage pump leakage, leakage, overload and over-temperature and other absolute protection, improve product safety and reliability.
- Float switch can be based on the required liquid changes, automatic control of submersible sewage pump start and stop, without special care, the use of extremely convenient
- QW (WQ) type sewage pump can be equipped with dual-rail automatic coupling installation system according to user's needs. It is very convenient for installation and maintenance. People do not have to enter the sewage pits for this purpose.
- can be used in the whole lift range, and ensure that the motor will not overload.
- QW (WQ) type submersible non-clogging sewage pump has two different installation methods, fixed automatic coupling installation system, mobile free installation system.
QW (WQ) type submersible non-clogging sewage pump structure description:
QW (WQ) type submersible non-clogging sewage pump consists of two parts of the motor and pump, the two separated by oil isolation chamber and mechanical seal components, is a mechanical and electrical integration products, motor and pump with the same axis (rotor) the entire pump length Short, compact. Equipped with a variety of protection devices, making the pump safe and reliable operation. The main components of the role as follows:
Signal line 1: equipped with full water pump control cabinet, the implementation of all-round protection of the pump, including leakage, phase, short circuit, overheating, motor overload and other projects.
Motor Stator 8: Class B or Class F insulation.
Leakage probe 11: The component is installed in the oil chamber, when the mechanical seal is damaged, the water into the oil chamber, the probe can send a signal from the control system to protect the pump.
Mechanical seal 13: the use of double-channel series seal, the choice of new hard corrosion-resistant tungsten carbide material, with a reliable seal, wear, long life and other characteristics.
Impeller 17: impeller with a single channel or dual flow channel structure, with a strong ability to pass through the large materials and fiber waste, to reduce the clogging, winding failure.
Pump body 15: equipped with the impeller, making the pump with high efficiency.
Seal ring 18: installed in the mouth of the pump body, when the impeller due to operation leaving the mouth ring wear, replace the seal ring to ensure the pump to the best efficiency.
QW (WQ) type submersible without clogging sewage pump Product use:
QW (WQ) type submersible non-clogging sewage pump for the factory business serious pollution of wastewater discharge, residential sewage sewage station, urban sewage treatment plant drainage system, air defense system drainage station, water plant water supply equipment, hospitals, hotels Sewage, municipal engineering construction site, exploration, mine supporting machine, rural biogas digesters, farmland irrigation and other industries, conveyor belt particles of sewage, dirt, can also be used for water and corrosive media.
QW (WQ) type submersible non-clogging sewage pump use and precautions:
- QW (WQ) type submersible non-clogging sewage pump should be carefully checked before use, whether the cable is damaged, fasteners are loose or fall off, the pump in the transport, storage, the installation process with or without deformation or damage.
- Measure the same and relative insulation resistance of the pump motor with 500V megger. The value should not be less than 2 megohms. Otherwise, the motor stator winding should be dried and the drying temperature should not exceed 120 ℃.
- The series of sewage pump installed fixed and mobile two. When using a fixed automatic installation, the chain should be inserted into (from the pump outlet, the connection should be parallel to the pump outlet) two hanging ring screws or lifting board up and down lifting pump. Evenly slow down along the guide until it is automatically coupled to the position. When using mobile installation, the first hose sets, with a chain into the two rings up and down lifting pump, pay attention to the cable can not be used as a rope to avoid danger.
- QW (WQ) type submersible non-clogging sewage pump connected after the rotation direction from the inlet as counterclockwise rotation, if the pump reversal, just the cable in any two lines to adjust the wiring position that can.
- QW (WQ) type submersible air-blocking sewage pump chassis ground must be strictly in accordance with the relevant procedures properly, in order to ensure the use of personal safety, in the pump running, is strictly prohibited in the vicinity of the installation, people do? Move, just in case the electric pump leakage accident.
- QW (WQ) type submersible non-clogging sewage pump in the absence of special circumstances must be equipped with automatic pump control cabinet, do not directly hang the grid or use the knife switch to turn on the power to ensure the normal operation of the pump.
- The pump should not be long-term operation in the low-lift state (generally use the head should not be less than 60% of the rated head), it is best to control the use of the proposed range within the lift to prevent the pump due to overload and burn the motor.
- No self-circulating cooling device pump is strictly prohibited the whole surface of the long-term operation to prevent overheating damage to the pump.
QW (WQ) type submersible non-clogging sewage pump installation, operation and maintenance:
- When installing and handling the pump, it is strictly forbidden to make the cable, so as not to cause the cable inside break, the connector is off-line, etc. The pump can not run normally, even burn the motor;
- Make sure that the grounding cable of the pump cable is properly grounded. When the pump is working, it is strictly forbidden to close the working area or touch the pump. In order to reduce the risk of electric shock, it can only be connected with the appropriate grounding socket.
- Do not overload operation;
- The cable used with the pump can not be less than 1.2 times the area of the pump cable;
- When installed, the pump must be fastened, but can not make the cable force, or with the pump start and stop when a rotation;
- run-time found that the pump is not water, you should check whether the pump is reversed, or pump outlet at the check valve inside the air is not drained;
- Regular inspection of the pump motor phase or relative between the insulation resistance, the value should not be less than 2MΩ, or should be disassembled;
- Electric pump in the specified working conditions, the normal operation after six months, should check the oil chamber sealing situation, such as oil in the oil is emulsified or water precipitation, should be replaced 10 # oil and mechanical seals;
- After a year of normal operation of the pump, it should be overhauled, replace the wear parts that have been worn and check the status of the fasteners. At the same time, replace the grease to ensure that the pump is well lubricated during operation.
- If the pump is not in use, please clean it and dry it.
QW (WQ) type submersible non-clogging sewage pump repair and maintenance:
- Pump should be hand management and use, and regularly check the pump winding and the insulation resistance between the chassis is normal.
- Each time, especially for thicker and thicker slurry, the pump should be placed in the water for several minutes to prevent the sediments left to ensure that the pump clean.
- If the pump is not used for a long time, the pump should be removed from the water, do not immerse in water for a long time to reduce the motor stator windings damp the opportunity to increase the life of the pump.
- In the conventional state of each pump after the use of 3 00 ~ 500 hours after the filling or replacement of oil in the oil tank (10 ~ 30 oil), so that the mechanical seal to maintain a good lubrication state, improve the mechanical seal life.
- After the pump is removed and repaired, the cabinet assembly must be inspected by 0.2MPa airtight test to ensure that the motor is sealed and reliable.
- The seal ring between the impeller and the pump body has a sealing function, such as sealing damage will directly affect the pump performance, if necessary, should be replaced.
QW (WQ) type submersible non-clogging sewage pumps Model significance:
QW (WQ) type submersible non-clogging sewage pump structure diagram:
- power cable
- motor connection
- junction box
- motor cover
- upper shaft seat
- motor housing
- shaft (rotor)
- oil and water probe
- oil chamber
- Mechanical seal
- rear cover
- pump body
- impeller bolts
- seal ring